Telecommunications Cabinet Freestanding 19 "42UR for communications switch and wiring.
For indoor use only in controlled air environment, it should not be placed outdoors.
Main structure consists of 1, 2 removable side, 1 Ceiling ventilated accessible wiring, 4 poles 9UR games, 4 Front and Back Doors needled, 3 intermediate trays and 4 horizontal supports for poles UR.
Manufacturing standards EIA-310D and NEMA 1. Sleeps 4 fans 4 slices of 2 " 4 leveling floor.
600 mm Front
1000 mm Depth
1985 mm Height
This sheet prepared in Carbon Steel SAE-1008, based on lime structure. 14 (1.9mm) 16 (1.5mm), front door lime. 18 (1.1 mm), rear doors and removable side cal.18 (1.1 mm), Lime ceiling. 18, and Poles for UR (Rack Units) cal. 14 (1.9mm), cal support posts. 16 (1.5mm).
4 sets of poles 9UR Mount Team in the body cabinet 1 ¾ or spacing 44.45mm (RMU) EIA-310D standard Universal standard for 19 "wide Includes 30 screws and nuts Caged 12/24 M6 for pole placement UR with foursquare kick. 4 compartment divided by input trays with wiring
Swash plate polyamide handle locked front door
Swash plate polyamide handle key to access later.
Four double bit locks for both sides for quick access.
1000 kg static load Construction:
Rigid base frames welded structure for stability and strength. rear and front doors with vertical frames a piece Zamak hinges for heavy-duty quick release.
Finishes: Polyester powder paint color, semi-matte black epoxy.